At Aquarden we use ion exchange in relation to utility – more precisely for wastewater treatment – both as part of a total solution or as a treatment method itself. Some examples include:
An example of how ion exchange is used as pre-treatment is cleaning of wastewater containing organic solvents with Aquarden’s SCWO system.
Ion exchange is used to exchange salts in the wastewater with hydrogen and hydroxide which forms water. This results in a higher capacity to a lower cost for the Aquarden SCWO system as the capacity is higher when the cleaning frequency is lower.
Read more in our case with Alfa Laval.
Ion exchange is also applicable as a stand-alone solution. For instance, in the metal finishing and surface treatment industry rinse water is recycled in order to reduce the amount of wastewater. The rinse bath often consists of three baths of which the last can use recycled water by purification with ion exchange.
Ion exchange can also be applied for polishing of wastewater after chemical treatment e.g. for removal of heavy metals. With the right choice of ion exchange resin, it is often possible to reduce the concentration of metals to a level that complies with the general discharge permit for municipal wastewater.
An ion exchange column contains a resin in which the exchange of the ions occurs. The resin can either be cation, anion, or a mix of both (mixed bed). A cation resin exchanges cations, and an anion resin exchanges anions. A mixed bed ion exchanger consists of both cation and anion resins and hence exchanges both.
The resin is placed in a column where the water is running upwards, which will generate a fluidized bed. In the illustration to the right the wastewater is pumped through the column containing a cation resin. When the cations of the wastewater pass through the cation resin the ion exchange occurs.
The resin consists of small particles which are made of a porous material with ion binding sites. The resin in the illustration is a cation resin with the cation A+ bound at the ionic binding sites. When the wastewater containing the cation B+ passes through the resin the cations are exchanged due to either:
The resin is constructed of an inert carrier material coated with an active chemical component with ion exchange properties. The inert carrier is normally cross-linked polystyrene. For standard ion exchange applications, it is sufficient to distinguish between strong and weak cation exchange resins as well as strong and weak anion exchange resins. However, other more special applications require resins with special properties and require expert consulting.
Standard resins have different affinity to ions and differ in which ions they exchange with. Therefore, the choice of resin depends on the specific case.
For instance, you can remove Ba+2, selectively in water with Ca+2, Mg+2 and Na+ by using a strongly acidic cation resin. This is not possible with a weak acidic cation resin. However, a strong acidic/basic resin uses more chemicals for regeneration therefore a weak resin should be used whenever possible.
Eden Aquatech AB Copyright © 2020
Biological water treatment